Views: 32 Author: pqwt Publish Time: 2023-01-05 Origin: PQWT
Now many homeowners choose to install floor heating, and are choosing water floor heating, heating effect is good, does not occupy the area does not affect the indoor aesthetics, but cleaning trouble, and because of the concealment, the occurrence of water leakage is also very difficult to deal with
Although the propaganda life of businessmen is decades long, but there are still leaks, so what are the reasons for leaks?
There are usually four reasons for floor heating.
1、Pipe quality problems
There are now countless manufacturers of underfloor heating products with varying quality
Some manufacturers will use raw materials of poor quality to make underfloor heating pipes, which are of poor quality for a short period of time and easily damaged due to the high temperature of underfloor heating pipes; poor processing accuracy and service life are not guaranteed
Therefore, when choosing floor heating products again, be sure to pay attention to choose a good brand
Floor heating installation is completed after the floor heating damage renovation
Although the installation of floor heating is completed after the pressure test, but in the subsequent renovation construction
Some renovation workers on the floor nail drilling and other carelessly punctured the pipe, or cut the floor tile when the pipe was sawed, which may lead to floor heating
Therefore, when installing floor heating, you should clearly communicate with the renovation company
Due to the lack of supervision, the industry is booming and too many construction teams are joining it, leading to uneven construction quality of the floor heating company itself, and even "guerrillas" without business licenses are invited to the home by the owners
Construction workers in the floor heating pipeline construction, not in accordance with the provisions of the operation, wearing pointed shoes construction, barbaric construction, careless, causing damage to the floor heating pipeline, construction is completed shall not be pressurized, to the back of the floor heating use of hidden dangers
Therefore, the floor heating construction to choose a professional company, test pressure after installation
The use of floor heating needs to be carried out under the specified temperature, the temperature is too high beyond the temperature range of the pipeline, and far more, it may lead to halving the life of the pipeline or even rapid rupture, there are interfaces because of thermal expansion and contraction and increase the gap
There are also wrong cleaning methods that can damage the pipes
Floor heating solutions
1: Analyze the possible causes of leaks by surveying the site.
2: Do a pressure test on the pipeline, do a pressure test must be playing water pressure, and to ensure that each corner valve faucet is in a closed state, close the main valve of the water pipe.
3: After confirming that there is indeed a problem with the pipe. Through drawings, experience or the use of auxiliary tools pipe towards the locator, to find out the specific location of the pipeline, distribution.
4: Put air pressure on the pipeline, the normal situation can be played 8 ~ 10 kg pressure, and then use a professional leak detector, along the location of the pipeline to test one by one to investigate, locate the location of the leak.
5: After determining the location of the leak point to excavate and repair.